Energy conversion and power generation has been a paramount and ever-evolving activity of man for several centuries. From simple wind-powered threshing mills, to coal-powered steam engines, power generation from natural gas, oil, renewable energy sources, and in recent time nuclear energy, man has constantly tried to improve. For developed countries, emphasis is laid on transition from non-renewable sources of energy to renewable sources with the aim of taming greenhouse effect and depletion of the ozone layer. For developing countries, such as Nigeria, it is a different ball game all together. Enough power is not being generated, let alone talks of transition. According to the Presidential Task Force on Power, “Nigerians are among the people most deprived of grid-based electricity in the world with a per capital consumption that is far lower than many other African countries”. Nigeria currently has the capacity to generate about 6000 megawatts of electricity of which only 3600 is being generated for a populace of over 160 million.
What this means is that about 22.8 Watts of electricity is produced for each Nigerian per capita. For all things being equal, Nigeria has the capacity to generate enough power to meet the power consumption needs of the populace. Small hydropower (SHP) is a proven technology that can stand-alone, being connected to an isolated grid, or the national grid. In most cases, it is often combined with irrigation systems. One of the major industrial problems in Nigeria is power generation. Sufficient power is not being generated to cater for industry needs, as well as the needs of the populace. Nigeria has the capacity to produce enough power to cater for the needs to industries and the populace at large. Aside being blessed with crude oil, solid minerals, and workforce, Nigeria is blessed with sufficient water bodies. While power from gas, steam, and coal is prevalent, the adverse effect of their usage cannot be overruled. Hydropower can contribute immensely in tackling the power situation in Nigeria. The bottom line is that SHP can adequately contribute to the electricity needs of Nigeria. Statistics prove that Nigeria is blessed with enough water bodies that can contribute substantially to power generation output. The exploitable hydropower potential in Nigeria is conservatively estimated to be about 10,000 MW  and only about 19% is currently been tapped or developed. The hydropower potential in Nigeria accounts for about 29% of the total electrical supply  . As at 2005, Nigeria had the capacity to produce 734.2 MW of electricity from SHP, but only 30 MW was being produced, which is less than 5% of what can be produced  . This work therefore aims at adding to the repertoire of knowledge and specifically designed small hydropower plant capable of supplying electricity for a small community using Ikere water gorge in Nigeria as a case study. Electricity generation is closely tied to economic, industrial and educational development. About 1.7 billion people do not have access to electricity  . If the issue of electricity is properly and effectively handled, there’s bound to be productivity in every aspect of the economy. If every community can handle its own power needs, the power supply from the national grid can be directed to major cities. Small hydropower has grown to become accepted as an inexpensive, easy to develop, and environmentally friendly source of energy. All of these benefits have increased the value of SHP options and have pioneered recent trends in renewable energy generation  . Hydropower is power or energy gotten from water. Flowing water at an elevation possesses the two forms of mechanical energy: potential and kinetic energies. Hydropower has long been harnessed prior to the widespread availability of commercial electric power. Over 2000 years ago, the Greeks used water wheels to grind wheat to flow  (US Department of Energy, 2008). Other ancient uses included irrigation, operation of textile machines, watermills, and sawmills. The concept of hydro-electricity became wide spread in the late 19th century with the coupling of waterwheels with electrical generators. As at the dawn of the 20th century, many towns, industries, and cities located near rivers had harnessed hydropower. In a country like the United States, as at 1920, about 40% of the power produced was from hydropower. This wide spread popularity gave hydropower the nickname “white coal”  . At the early stages of the development of hydropower plants, they were relatively more reliable and efficient than fossil fuel-powered plants  . This can be held accountable for the proliferation of small and medium-sized hydropower plants wherever there was sufficient moving water and a need for electricity. As the population of the world increased, the demand for electricity grew, leading to an increased number and size of fossil fuel, hydropower, and even nuclear power plants. In recent years due to the size of hydropower plants, associated dams and reservoirs have been developed with additional uses such as irrigation, recreation, navigation, flood control, and water supply. Conversely, hydropower plants have been incorporated to dams that were originally built for irrigation, water supply, and flood control. Despite the seemingly high potential of hydropower, it accounts for about 16.3% of the world’s electricity, which is lesser than power generated from fossil fuels. Fossil fuel plants account for about 67.2% of the world’s electricity. However, power generated from hydro is higher than nuclear, wind, solar, geothermal, and other sources of power combined  . Concerns about the environment and social impact of using fossil fuels have considerably increased in the last decades. These concerns have lead to increased campaigns on shifting towards greener and more environmental energy source. As earlier stated hydropower provides the largest share of renewable electricity worldwide and still has enormous potential for future development. As at today, hydropower plants span from few Watts to several Gigawatts. The largest projects are Itaipu in Brazil (14,000 MW) and Three Gorges in China (22,400 MW).
2. Mechanism of Hydropower
The definition of small hydropower varies from country to country, as there is no internationally accepted value. In a country like Sweden, the limit is 1.5 MW, in India 15 MW, and in China, small hydropower encompasses capacities up to 25 MW. However, 10 MW is generally accepted as the threshold for small hydropower by European Small Hydropower Association, European Commission, and International Union of Producers and Distributors of Electricity  . Small hydropower projects can be further broken down as; mini, micro, and pico hydropower depending on the installed capacity. These limits are 1 MW, 100 kW, and 16 kW for mini, micro, and pico hydropower, respectively  . Table 1 shows hydropower definitions according to ECOWAS.
The 30 MW limit for small hydropower was because all the projects in the considered region were added up (ECREEE, 2012).
2.1. Advantages and Disadvantages of Small Hydropower Plant
 stated that “SHP meets the needs of the present without compromising the ability of future generations to meet their own needs.” What this means is that small hydropower is sustainable. When compared with other sources of power, small hydropower ranks amongst the cheapest. Aside the fact that SHP has high untapped potential, especially in developing countries, its technology is open to new technological developments. Another major advantage is its flexibility and reliability, as well as its independence on the fuel costs. It has fast start up and shutdown response time  . According to  , “one GWh of electricity produced by small hydropower means a reduction of 480 tonnes of emitted carbon dioxide”. What this implies is that, when compared with other sources of electricity, small hydropower is very much environmental friendly. In addition, small hydropower schemes have long life spans and after building and installations, the associated cost and frequency of maintenance are minimal  . Small hydropower plants however do not come without disadvantages. One of such disadvantage is the effect of small hydropower schemes on fishes. Weir and intake structures disrupt the movement of fishes. There is also the possibility of fishes being killed by the turbine blades or gas bubbles from supersaturated water. Another disadvantage is variation in energy production due to seasonal variations in flow. Unlike other sources which have more stable and fixed electricity generation capacity, variations in flow (during low flow seasons) limit electricity generation  .
Table 1. Definition of hydropower.
2.1.1. Small Hydropower in the World
Small hydropower contributes immensely to the worlds’ renewable energy sources because it is cheap and provides clean energy. Table 2 shows the global contribution of each renewable energy source.
Going by the definition of small hydropower being between 1 MW - 10 MW, as at 2004, the total globally installed small hydropower plants produced about 48 Gigawatts (GW), as shown in Table 3. China is one of the worlds’ largest users of small hydropower. As at 2005, China had reached a power production capacity of 31,200 MW which accounts for more than half of what is being produced worldwide  . Despite this promising figure, there are still several untapped small hydropower potential in several countries and continents, especially in Africa and Asia. In Canada moves have been made to replace diesel generators by SHP in remote, off-grid regions  (Figure 1).
2.1.2. Small Hydropower in Nigeria
As stated in preceding sections, economic development of a country is closely tied to its ability to provide enough power to cater for the domestic and industrial needs of the populace. In Nigeria however, the demand for power far
Figure 1. Value of K for different bar shapes (BIS, 2012).
Table 2. Global contribution by each renewable energy source  .
Table 3. Installed SHP (<10 MW) capacity by world region in 2004  .
outstrips the power being generated and supplied. Nigeria has numerous potential sites for SHP. Harnessing these options will go a long way in changing the power production level in Nigeria. Between 2003 and 2007, Nigeria experienced a growth in hydropower of 9.7%  . As at 2005, although Nigeria had the capacity to produce 734.2 MW of electricity from SHP, only 30 MW was being produced, which is less that 5% of what can be produced  (ECN-UNDP RE Master Plan, 2005). Owing to the fact that most Nigerian communities have SHP potentials, power generated from SHP projects can be used to supply electricity for lighting, information and communications technology, and processing of agricultural produce. The underlying assumption is that these SHP projects can sufficiently provide power for rural communities, while feeding the excess to the national grid. According to the National Agency for Science and Engineering Infrastructure (NASENI) SHP capacity in Nigeria can reach 3500 MW, accounting for about 23% of the country’s entire hydropower capacity  . Table 4  reveals potential sites for SHP projects in Nigeria.
3. Data, Equations and Calculation
Results were obtained using the standard hydropower equations with the data obtained from the site (Ikere gorge Dam) coupled with some other fundamental fluid property values  . The Aerial view of Ikere gorge dam site using Google maps is as shown in Figure 2 and Figure 3. The analysis done to obtain the results is as follows.
Figure 2. Aerial view of Ikere gorge dam using Google maps.
Figure 3. Aerial view of Ikere gorge dam using Google maps.
Table 4. Summary of small hydropower potential sites in Nigeria  .
Theoretical Power (Pth)
The theoretical power is the maximum power that can be generated from the hydropower project. The assumption is that the efficiency of the system is 100%, as well as no head losses.
The theoretical power is calculated using equation below
Pth = ηρgQH
η = 1
ρ = 1000 kg/m3
g = 9.81 m/s2
Q = 31.8 m3/s
H = 30 m
Penstock Diameter (D)
Selection of the diameter size of a penstock is interplay between limiting head losses and reducing the cost of the penstock. The head losses decrease as the penstock diameter increases. On the contrary, the cost of penstock increases with an increase in diameter.
The penstock diameter is calculated such that the overall head loss is limited to 4%. This is given by Equation (3.3) as.
n = 0.009 for PVC
Q = 31.8 m3/s
L = 100 m
Hgross = 30 m
When the head losses―loss at intake, loss at trash rack, frictional losses, losses through bends, and loss at gate valve were calculated using this value (2.1 m), it was discovered that the total head losses exceeding the acceptable range limit of 4%. Different values of D were computed―2.1 m, 2.2 m, 2.3 m, 2.4 m, 2.5 m, and 2.6 m. At 2.6 m, the total head loss was within the limit of 4%.
Hence, D = 2.6 m
Minimum Thickness (tmin)
A supplier recommended 15mm, hence the choice for a penstock thickness of 15 mm.
Velocity in Penstock (V)
V = Q/A
Q = 31.8 m3/s
A = 3.142 × 2.62/4 = 5.31 m2
Head Loss at Intake (hi)
K is a constant and is given as 0.04 for this design
V = 5.99 m/s
g = 9.81 m/s2
Frictional Loss (hf)
The frictional loss is given by equation
L = 100 m
n = 0.009
Q = 31.8 m3/s
D = 2.6 m
Head Loss at Bend (hb)
Kb is a constant and is given as 0.085 for this design
V = 5.99 m/s
g = 9.81 m/s2
Loss at Gate Valve (hv)
Kv is a constant and is given as 0.15 for fully opened gate valve
Pressure Wave Velocity (c)
The surge pressure wave velocity is given by Equation (3.8)
K = 2.1 × 109 N/s2
E = 2.75 × 109 N/m2
D = 2600 mm
t = 15 mm
Critical Time (T)
Surge Pressure in Penstock (ps)
The surge pressure is given as:
Surface Area (S)
The surface area of the trash rack is as given below:
K1 = 0.85 for an automatic raker
b = 70 mm
a = 60 mm
The approach velocity, V0 is limited to 1.5 m/s since there are plans to make use of mechanical raking system.
α = 60˚
Head Loss through Trash Rack (ht)
Ks = 1.67 for flat bar with rounded ends as seen in Figure 1
tb = 12 mm
Power Output (p)
The power output the turbine is given as (P)
P = ηρgQHn
η = 0.9
ρ = 1000 kg/m3
g = 9.81 m/s2
Q = 31.8 m3/s
Hn = 28.86 m
Specific Speed (nQE)
The rotational speed of a Kaplan turbine is given by equation
Rotational Speed (n)
The rotational speed is calculated from equation below
Runway Maximum Speed
The runway maximum speed for a Kaplan turbine is given as:
Runner diameter (De)
Hub diameter (Di)
Cavitation coefficient (σ)
Suction head (Hs)
Patm = 98,000 Pa
Pv = 3493.04 Pa
4. Cost Analysis
Cost analysis was carried out using the fundamental equations  .
Annual Energy Output (E)
The annual energy output is given as a function of
Qmedian = flow in m3/s for incremental steps on the flow duration curve
Hn = Specific net head
ηturbine = turbine efficiency
ηgenerator = generator efficiency
ηgearbox = gearbox efficiency
ηtransformer = transformer efficiency
γ = specific weight of water
h = number of hours in a year
Annual Energy Generation
The annual energy generation is given as:
Annual Energy Yield (kWh) = capacity factor × Power (kW) × Hours in a day × Days in a year
Annual Energy Yield (kWh) = 0.5 × 8130 kW × 24 hours × 365 days = 3.6 × 107 kWh
The current rate of electricity in Nigeria is ₦ 16.11 per kWh.
Hence, Annual generated revenue = Annual Energy Yield × Rate
=3.6 × 107 × 16.11
Design Head, H: 30 m
Flow Rate, Q: 31.8 m3/s
Theoretical Power, Pth: 9.36 MW
5.1. Penstock Design
Material: Polyvinyl Chloride Pipe
Length, L: 100 m
Diameter, D: 2.6 m
Minimum thickness, tmin: 7.7 mm
Penstock thickness, t: 15 mm
Velocity in Penstock, V: 5.99 m/s
Head loss at penstock inlet, hi: 0.073 m
Frictional loss in penstock, hf: 0.517 m
Head loss at bends, hb: 0.155 m
Loss at gate valve, hv: 0.274 m
Pressure wave velocity, c: 125.49 m/s
Critical time, T: 1.59 sec
Surge pressure in penstock, Ps: 51.22 m
5.1.1. Trash Rack
Configuration: Type 1
Approach velocity to trash rack, V0: 1.5 m/s
Inclination to the horizontal, α: 60˚
Bar Spacing, b: 70 mm
Bar thickness, tb: 12 mm
Bar width, a: 60 mm
Total surface area, S: 62 m2
Head loss through trash rack, ht: 0.015 m
Selected turbine: Kaplan
Power output: 8.13 MW
Rotational speed: 6.1 s−1
Specific speed: 0.5
Runway Maximum Speed: 19.52 s−1
Runner diameter: 1.98 m
Hub diameter: 0.87 m
Cavitation coefficient: 0.623Suction head: −6.577 m
5.1.3. Estimated Cost
Preparation of Site: ₦ 2,000,000
Civil Works: 6,000,000
Penstock: ₦ 15,660,000
Control System: ₦ 500,000
Turbine: ₦ 8,439,000
Generator: ₦ 4,000,000
Exciter: ₦ 3,700,000
Protection System: ₦ 700,000
DC Emergency Supply: ₦ 1,000,000
Transformer: ₦ 15,000,000
Installation: ₦ 4,500,000
Total Cost: ₦ 61,499,000
Miscellaneous/Unforeseen expenses: 3%
= ₦ 1,844,970
Total Cost: ₦ 63,343,970
5.1.4. Annual Revenue
The annual revenue is defined as the gross average annual energy output multiplied by the estimated cost of energy per kilowatt (kw/hr) minus the cost incurred as a result of downtime. Downtime is any period the SHP is not functioning either due to maintenance reasons or shortage of water.
Annual Energy Output: 3.6 × 107 Kilowatt hour
Estimated Annual Revenue: ₦ 579,960,000
Estimated Yearly Cost of Maintenance: ₦ 500,000
6. Conclusions and Recommendations
In conclusion, this work has been able to establish that Ikere gorge Dam in Nigeria is a feasible site for a small hydropower plant. Small hydropower plant capable of supplying electricity for a small community using the gorge as a case study has also been designed. Estimated power generation capacity of the designed SHP is 9.36 MW. While the estimated total cost of the plant is ₦ 63,343,970, the plant annual deliverable expected revenue estimated is ₦ 579,960,000 with annual power yield of 3.6 × 107 kWh/yr.
It is clear that adoption of small hydropower schemes is a viable source towards increasing the power generation capacity of Nigeria. However, the underdevelopment in small hydropower is tilted towards certain governmental policies and their implementation than towards the unavailability of the technology. As a result, the following recommendations are made with regards to small hydropower. In order to reduce the overall cost of purchasing SHP components, local manufacturing capacity needs to be sorted after, encouraged and tested. Deregulation in the upstream and downstream sectors, such as private investors, are encouraged to invest in power generation.
 UNIDO. (2006) The Nigerian Capacity to Host the Regional Centre for SHP, UNIDO Regional Center for Small hydro Power, Abuja, Nigeria.
 Kumar, A.T., Schei, A., Ahenkorah, R., Caceres Rodriguez, J.-M., Devernay, M., Freitas, D. and Hall, Å. (2011) Hydropower. IPCC Special Report on Renewable Energy sources and Climate Mitigation. Cambridge University Press, Cambridge, United Kingdom and New York, NY, USA.
 Kadner, S., Zwickel, T., Eickemeier, P., Hansen, G., Schlömer, S. and von Stechow, C. (2011) Hydropower. IPCC Special Report on Renewable Energy Sources and Climate Mitigation. Cambridge University Press, Cambridge, United Kingdom and New York, NY, USA.