Analysis of Non-Sinusoidal Steady Electric Field of ±500 kV Converter Transformer

Gang Liu^{1}^{*},
Cheng Chi^{1},
Yanjiao Jin^{1},
Yongqiang Ma^{1},
Lipeng Sun^{1},
Lin Li^{2},
Youliang Sun^{3}

Show more

The line side winding is under the fundamental frequency AC voltage, while the valve side winding contains not only fundamental AC voltage component, but also the DC voltage component, fundamental AC voltage component, and higher harmonic voltage components when the converter transformer is at its normal operating condition, and the electric field of converter transformer is a non-sinusoidal steady one. To analyze the non-sinusoidal steady electric field containing the DC component, fundamental AC and higher harmonic components, the voltage spectrum of the valve winding in a ±500 kV converter transformer is firstly analyzed, and the non-sinusoidal periodic steady electric field is obtained by the fast discrete Fourier transform. Different resistivity of the oil and oil-immersed paper is adopted to simulate the aging of oil paper insulation at operation, and get the non-sinusoidal steady electric field.

References

[1] Zhao, W.J. (2004) HVDC Engineering Technology. China Electric Power Press, Beijing, 318-325.

[2] Wang, C.L. and Li, J.H. (2005) Calculation and Analysis of End Electrical Field in Valve Winding Polarity Reverser Test for Converter Transformer. Transformer, 42, 11-14.

[3] Kurita, A., Takahashi, E., Ozawa, J., et al. (1983) DC Flashover Voltage Characteristics and Their Calculation Method for Oil-Immersed Insulation Systems in HVDC Transformers. IEEE Transactions on Power Delivery, PWRD-1, 184-190.

[4] Lv, X.D. and Chen, D.L. (1997) TheStudy on Electric Field Characteristics of Converter Transformer under Polarity Reversal. High Voltage Engineering, 23, 67-72.

[5] Zhang, Y.L. and Xie, D.X. (2001) Analysis of Transient Electric Field in Converter Transformer. Journal of Shenyang University of Technology, 23, 467-470.

[6] Li, J., Luo, L.F., Xu, J.Z., et al. (2016) Study on Electric Charateristics at Ends of Valve Side Winding in Converter Transformer. High Voltage Engineering, 32, 121- 214.

[7] Chen, Q.G., Zhang, J., Gao, Y., et al. (2008) Analysis of Complex Electric Field on Valve Side Widing of Converter transformer. High Voltage Engineering, 34, 484- 488.

[8] Ding, Z.G., Li, G.F., Li, P., et al. (2008) Electric Field Characteristic Calculation on Typical Oil-Paper Combination Insulation under Polarity Reversal. Power System Technology, 32, 82-85, 90.

[9] Zhang, X.L., Wang, J.M., Wu, Z.B, et al.(2009) Numerical Analysis of Electric Field in Valve Side Lead-out Wire for UHV DC Converter Transformer. Transformer, 46, 1-4, 10.

[10] Liu, P., Peng, Z.R., Dang, Z.P., et al. (2009) Study on Electric Field Distribution of ±800kV Converting Transformer Bushing Outlet Terminal during Polarity Reversal Test. Insulators and Surge Arresters, 3, 1-4, 8.

[11] Fu, T.J., Wang, J., Zhong, J.T., et al. (2009) Insulation Structure Analysis of ±800kV Converter Transformer for DC Transmission. Transformer, 46, 1-5.

[12] Zhang, Y.B., Zheng, J., Wang, D.H., et al. (2010) Development of UHVDC Converter Transformer. High Voltage Engineering, 36, 255-264.

[13] Liu, G., Li, L., Li, W.P., et al. (2012) Analysis of Nonlinear Electric Field of Converter Transformer under Polarity Reversal Voltage. High Voltage Engineering, 38, 451-456.

[14] Li, Y., Li X.H., Tang, C., et al. (2012) Analysis on Transient Electric Field at Ends of Valve-Side Winding in Converter Transformer. High Voltage Engineering, 38, 2797-2804.

[15] Li, L., Ji, F., Li, W.P., et al. (2011) Numerical Simulation of Converter Transformer’s Polarity Reversal Test. Proceeding of the CSEE, 31, 107-112.

[16] Hou, X.M. (2013) The Electric Field Charateristics Simulation of Converter Transformer Valve Side and Analysis of Its Influence Factors. Shenyang University of Technology, Shenyang.

[17] Liu, G., Li, L., Zhao, X.J., et al. (2012) Analysis of Nonlinear Electric Field of Oil- Paper Insulation under AC-DC Hybrid Voltage by Fixed Point Method Combined with FEM in Frequency Domain. Proceeding of the CSEE, 32, 154-161.

[18] Zhang, H.F., Liu, G. and Li, H.Q. (2015) Simulation Analysis on Winding Current of Three-Chang ±500kV Converter Transformer under Different Operating Conditions. Shanxi Electric Power, 43, 46-50.

[19] Haus, H.A. and Melcher, J.R. (1992) Electomagnetic Fields and Energy, Translated by Jiang, J.L., Zhou, P.B., Qian, X.Y., et al., High Education Press, Beijing, 9-26. (In Chinese)

[20] Yuan, J.S. (1991) Method of Finite Element-Fast Fourier Transformation for Calculation of Linear Time-Dependent Eddy Current Fields. Journal of North China Institute of Electric Power, 43-50.