Capacitance of Water Tree Modeling in Underground Cables
Abstract: Water Tree is a corrosion phenomenon in cross-link polyethylene (XLPE) insulation. It is commonly found in underground cables. Water tree induced fault is difficult to detect due to its high impedance and difficult to model due to its random nature. In recent years, underground cables have become more popular in the power industry. They are resistant to environmental damage and has reduced space requirement. They are suitable to areas with high environment hazard or heavily populated areas where space is a constraining factor. As a result, studying and modeling the structure and effect of water tree become increasingly important. Since majority of the fault inducing water trees are vented trees which originated from the surface of the cable insulation, the mathematical model focuses on this particular type of water tree. To reduce the complexity of the model, the shape of the water tree afflicted region of the insulation is assumed to be ellipsoidal and the permittivity of the region is assumed to be linearly changing. Finite element analysis is used to analyze the water tree affected region. The resultant capacitance is calculated and compared with a physical model from Comsol. The result obtained using the proposed mathematical model and the result obtained using physical simulation through Comsol package agrees with each other. Hence, this method can be used to analyze the effect of water tree fault in large power systems.
Cite this paper: Chen, Q. , Burkes, K. , Makram, E. , Hadidi, R. and Xu, X. (2014) Capacitance of Water Tree Modeling in Underground Cables. Journal of Power and Energy Engineering, 2, 9-18. doi: 10.4236/jpee.2014.211002.
References

[1]   Xu, L. and Brown, R.E. (2009) A Framework of Cost-Benefit Analysis for Overhead-to-Underground Conversions in Florida. Power & Energy Society General Meeting, 2009. PES '09. IEEE, Calgary, 26-30 July 2009, 1-7. http://dx.doi.org/10.1109/PES.2009.5275583

[2]   Park, S.-H., Jung, H.-E., Yun, J.-H., Kim, B.-C., Kang, S.-H. and Lim, K.-J. (2008) Classification of Defects and Evaluation of Electrical Tree Degradation in Cable Insulation Using Pattern Recognition Method and Weibull Process of Partial Discharge. International Conference on Condition Monitoring and Diagnosis, 2008. CMD 2008, 21-24 April 2008, Beijing, 101-104.
http://dx.doi.org/10.1109/CMD.2008.4580240

[3]   Lee, J.D., Ryoo, H.S., Choi, S.B., Nam, K.Y., Jeong, S.H. and Kim, D.K. (2006) H/W Desig for Fault Location System on Underground Power Cable. Transmission and Distribution Conference and Exhibition, 2005/2006 IEEE PES, 21-24 May 2006, Dallas, 843-846.
http://dx.doi.org/10.1109/TDC.2006.1668607

[4]   Ponniran, A. and Kamarudin, M.S. (2008) Study on the Performance of Underground XLPE Cables in Service Based on Tan Delta and Capacitance Measurements. Power and Energy Conference, 2008. PECon 2008. IEEE 2nd International, 1-3 December 2008, Johor Bahru, 39-43.
http://dx.doi.org/10.1109/PECON.2008.4762442

[5]   Livie, J., Gale, P. and Wang, A.D. (2008) The Application of On-Line Travelling Wave Techniques in the Location of Intermittent Faults on Low Voltage Underground Cables. IET 9th International Conference on Developments in Power System Protection, 2008. DPSP 2008, 17-20 March 2008, Glasgow, 714-719.

[6]   Pandey, A. and Younan, N.H. (2010) Underground Cable Fault Detection and Identification via Fourier Analysis. 2010 International Conference on High Voltage Engineering and Application (ICHVE), 11-14 October 2010, New Orleans, 618-621. http://dx.doi.org/10.1109/ICHVE.2010.5640779

[7]   Long, Z.L., Younan, N.H. and Bialek, T.O. (2012) Underground Power Cable Fault Detection Using Complex Wavelet Analysis. 2012 International Conference on High Voltage Engineering and Application (ICHVE), 17-20 September 2012, Shanghai, 59-62.
http://dx.doi.org/10.1109/ICHVE.2012.6357058

[8]   Gilany, M., Ibrahim, D.K. and Eldin, E.S.T. (2007) Traveling-Wave-Based Fault-Location Scheme for Multiend-Aged Underground Cable System. IEEE Transactions on Power Delivery, 22, 82-89.
http://dx.doi.org/10.1109/TPWRD.2006.881439

[9]   Steennis, E.F. and Kreuger, F.H. (2002) Water Treeing in Polyethylene Cables. IEEE Transactions on Electrical Insulation, 25, 989-1028. http://dx.doi.org/10.1109/TPWRD.2006.881439

[10]   Maeda, T., Kaneko, D., Ohki, Y., Konishi, T., Nakamichi, Y. and Okashita, M. (2004) Effect of the Applied Voltage Frequency on the Water Tree Shape in Polyethylene. Proceedings of the 2004 IEEE International Conference on Solid Dielectrics, 2004. ICSD 2004, 1, 276-279.
http://dx.doi.org/10.1109/ICSD.2004.1350344

[11]   Hwang, B.K. (1990) A New Water Tree Retardant XLPE. IEEE Transactions on Power Delivery, 5, 1617-1627. http://dx.doi.org/10.1109/61.58008

[12]   Leslie, Y.Y., Dmitri, L., Shau-Chun, W. and Hsueh-Chia, C. (2004) A New AC Electrospray Mechanism by Maxwell-Wagner Polarization and Capillary Resonance. Physical Review Letters, 92, Article ID: 133902.

[13]   Koo, J.Y., Cross, J.D., El-Kahel, M., Meyer, J.C. and Filippini, J.C. (1983) Annual Report of the Conference on Electrical Insulation and Dielectric Phenomena. 301.

[14]   Filippini, J.C., Koo, J.Y. and Chen, J.L. (1989) Electrode Influence on the Propagation of Water Trees in Polyethylene. IEEE Transactions on Electrical Insulation, 24, 75-82.
http://dx.doi.org/10.1109/14.19868

[15]   Burkes, K., Makram, E.B. and Hadidi, R. (2014) Water Tree Detection in Underground Cables Using Time Domain Reflectometry. Department of Electrical and Computer Engineering, Clemson University, Clemson. (Unpublished)

[16]   Burkes, K. (2014) Water Tree Analysis and On-Line Detection Algorithm Using Time Domain Reflectometry. Master’s Thesis, Clemson University, Clemson, 29634.

Top